New Construction / UK / 2018 /
02 Health and Wellbeing
Information correct as of 23rdJune 2021. Please see kb.breeam.com for the latest compliance information.
00 Blank note - KBCN0997
Please note: If there are no other compliance notes below this one it simply means that none exist yet for this issue.
Air-conditioned spaces - KBCN00035
Air-conditioned spaces are assessed to ensure appropriate thermal comfort levels are achieved. Cooling capacity should be sufficient to comply with the requirements of CIBSE Guide A, however providing sufficient space to install additional capacity to meet the requirements at a later date in line with projected climate change scenarios is also acceptable.
In addition, if it can be demonstrated that the air-conditioning system can achieve the thermal comfort criteria in accordance with CIBSE Guide A, Table 1.5, thermal modelling does not need to be carried out. The “time out of range” (TOR) metric should be reported as 0%.
Alternative weather files - KBCN1182
Different or newer weather files can be used instead of those referenced in the manual, as long as they achieve the aim of the credit. Weather files based on climate projections with higher temperatures than those specified in the relevant criteria, set a more robust standard for overheating and so they are acceptable. The alternative weather files need to include same variables as the specified weather files e.g. dry bulb & wet bulb temperature, wind speed & direction, solar altitude & azimuth, cloud cover etc. for each hour of the year. It is the role of the assessor or design team to verify this and ensure that meeting the BREEAM criteria does not become easier by using the alternative weather file.
ANC membership/registration scheme compliance route - KBCN0246
The Association of Noise Consultants (ANC) registration scheme is only applicable to buildings covered in Approved Document E. It therefore covers Dwellings-Houses, flats and rooms for residential purposes and schools, and so would only apply to assessments that contain these room types. For these assessments, if the suitably qualified accoustician is a member of the ANC, they must also provide evidence to demonstrate that they are a full member of the ANC registration scheme.
For all other building/room types, assessors can still demonstrate compliance by the other routes listed in the manual.
Applying the requirements to Shell & Core assessments - KBCN00075
A Suitably Qualified Acoustician (SQA) must carry out a quantifiable assessment of the specification of the built form, construction and any external factors that are likely to affect the indoor ambient noise levels. From this assessment, the SQA must confirm that the developer’s scope of works will enable a future tenant utilising a typical fit-out and specification to meet the levels required to demonstrate compliance with the BREEAM criteria.
Where the specific room functions and areas within the building are yet to be defined, the acoustician’s assessment should demonstrate that the criteria for the most sensitive room type likely to be present in the building is capable of being achieved. Where the typical fit out would include a range of requirements (e.g. offices with a mix of open plan, cellular offices, meeting rooms and breakout areas; or retail with sales floor, stock/storage, office and staff rest areas), the acoustician should make an assessment based on a speculative layout and outline specification to determine whether the requirements of the relevant best practice standard are achievable and include examples of the most sensitive room types.
Where the majority of a building’s floor plan will require high performance acoustic environments (e.g. classroom/seminar buildings), then the BREEAM requirements must be achieved for the entire shell where specific layouts are not determined by the built form.
Post-construction testing is not required subject to confirmation from the project team that the built form, construction and any external factors have not changed from those used in the SQA's assessment.
09/08/2019 Confirmed applicability to UK NC 2018
08/12/2017 Clarification added regarding post-construction evidence.
Associate membership of the Institute of Acoustics - KBCN00064
Associate membership of the Institute of Acoustics (IOA) is not sufficient to demonstrate that the individual is a member of an appropriate professional body, to meet the requirements of a suitably qualified acoustician (SQA).
The following is stated on the IOA website about Associate Membership; 'this class of membership is aimed primarily at persons who have obtained the appropriate academic qualifications for the grade of Member but who do not (yet) have the relevant period of experience in the profession for the grade of Member.'
13/01/2020 Wording clarified and confirmed applicability to Issue Pol 05
06/01/2020 Clarification that this applies to BREEAM UK NC2018
Compliant test body – alternative compliance route using a Suitably Qualified Acoustician - KBCN1412
Where acoustic testing and measurement has not been performed by an organisation or individual that meets the definition of a compliant test body, compliance with this requirement can still be demonstrated where a Suitably Qualified Acoustician has reviewed the relevant test report(s).
The test report must:
a) Be countersigned or authorised by a Suitably Qualified Acoustician
b) Include a clear statement that the acoustic testing and measurements have been carried out in accordance with the BREEAM or HQM testing requirements
c) Include evidence that the verifier meets the definition for a Suitably Qualified Acoustician within the relevant BREEAM or HQM technical manual
Control of glare from sunlight – ‘openness factor’ of blinds - KBCN1446
The ‘openness factor’ or ‘openness coefficient’ is the ratio between the area of openings and the total area of fabric. It is one of the factors in determining how much light will pass through the fabric of the blind.
For example, ‘black-out blinds’ may have an openness factor/coefficient of 0%.
For further details, please refer to: BS EN 14501:2005 ‘Blinds and shutters — Thermal and visual comfort — Performance characteristics and classification’
Control of glare from sunlight – adjacent buildings - KBCN1248
It is acceptable to account for surrounding buildings, structures or other permanent environmental features when using simulation modelling to assess the risk of glare, provided this accounts for both direct sunlight and reflected glare from glazing or reflective surfaces.
This KBCN aligns with KBCN1211 from UKNC 2014
Control of glare from sunlight – blackout blinds - KBCN1246
Blackout blinds can be used to meet the glare control requirements.
Where the criteria set an upper limit for transmittance value, but no lower limit, blackout blinds will meet this requirement.
This KBCN aligns with KBCN0447 from UKNC 2014
Control of glare from sunlight – hotel rooms - KBCN1087
The primary function attributed to hotel rooms is that of a bedroom and as such, lighting and resultant glare are not considered to be problematic for these spaces.
The only exception to this is where designated additional office space is provided. In these circumstances it is the role of the assessor to determine if individual spaces should be determined as ‘relevant building areas’ in accordance with guidance provided.
Glare control criteria apply to building areas where lighting and resultant glare could be problematic for users.
This KBCN aligns with KBCN0666 from UKNC 2014
Control of glare from sunlight – no relevant building areas - KBCN1086
If the scope of the assessment does not include any relevant building areas, as defined within the manual, the criteria for Control of glare from sunlight can be considered as met by default.
Only spaces that fall within the definition of relevant areas and are within the assessment’s scope need to be assessed.
This KBCN aligns with KBCN0429 from UKNC 2014
Control of glare from sunlight – residential areas - KBCN1092
Control of glare from sunlight criteria apply to building areas where lighting and resultant glare could be problematic for users. In residential buildings this would include areas such as study bedrooms or facility management offices, where work or study will be carried out and where glare would hinder such activities. It does not apply to other residential areas.
This KBCN aligns with KBCN00040 from UKNC 2014
Control of glare from sunlight – roof lights - KBCN1091
Where roof lights are present, they must be considered when demonstrating that the glare control strategy provides adequate control/measures for minimising glare in that space.
All sources of glare need to be considered when designing out the potential for disabling glare.
This KBCN aligns with KBCN0319 from UKNC 2014
Control of glare from sunlight – transmittance value - KBCN1089
Transmittance values should be based on those quoted for ‘visible' or 'optical' light transmittance.
23 Mar 2021 - Reference to the term 'optical' added, for clarity
This KBCN aligns with KBCN0709 of UKNC 2014
Control of glare from sunlight – types of glare - KBCN1043
Assessors should ensure that the design team has considered the possibility of glare from all sources, including direct sunlight, reflected sunlight and contrast glare.
Control of glare from sunlight – use of tinted windows - KBCN1090
Solar control or ‘tinted’ glazing could potentially support the attainment of this requirement. However, the assessor must be satisfied and provide evidence to demonstrate that the particular glazing type, when used on the assessed building for a given location, is meeting this overarching aim of preventing disabling glare. It should be noted that whilst certain types of glazing, such as low emissivity glazing, may be slightly tinted, they may not necessarily be effective in reducing disabling glare.
For facades receiving direct sunlight, tinted windows alone are unlikely to be sufficient in the majority of situations.
This KBCN aligns with KBCN0862 from UKNC 2014
Control of glare from sunlight- no windows in relevant areas - KBCN1088
Where a ‘relevant area’ as defined in the manual does not include any windows, the glare control criteria can considered as met for this area.
Note that the view out and daylight criteria would not be achieved in rooms with no windows.
Where there are no windows in a room there would be no potential for disabling glare, so the aim of the credit would be achieved.
This KBCN aligns with KBCN0146 of UKNC 2014
Daylighting – speculative building - KBCN0269
Where the building is speculative and therefore the final layout is not defined (e.g. only an open plan shell is provided in each tenanted space), the required percentage of each open plan shell should meet the daylighting requirements. However, where it is possible to designate separable ancillary areas that would be required in the space (such as toilets or server room), these can be excluded from the calculation.
For daylight calculations in speculative projects where the layout and colours are unknown, a realistic notional layout may be used.
Daylighting – ‘Internal association or atrium areas’ - KBCN1267
This term refers to areas intended to replace outdoor recreation spaces, typically found in prisons, but which may also be present in hospitals and residential accommodation for elderly people.
The requirements relating to such spaces are, therefore, not generally applicable to other building types.
Daylighting – alternative route to compliance - KBCN1047
The alternative route was developed for rooms in Healthcare developments with multiple functions within the same space, and as such, having different daylight needs at various points within the room.
For other building types, an assessor wishing to use the alternative route to compliance for daylighting should contact the BREEAM technical team with details and justification.
The alternative route was applied to Healthcare building types specifically because these building types are likely to have spaces that have varying needs for daylight. For example, in a hospital ward, the areas where patient beds are located will benefit from good daylight, whereas this is of less importance for the nurses stations, which are used intermittently.
Daylighting – Changing rooms - KBCN1132
The daylighting criteria are not applicable to changing rooms.
Daylighting – communal kitchens (multi-residential) - KBCN0217
Communal kitchens should be assessed under 'Non-residential / Communal Occupied Spaces.
Communal kitchens outside of self-contained dwelling units, for example a kitchen within a self-contained student flat shared between several students would be classed as a private kitchen for the purposes of this issue. However, if it was shared between rooms along a communal corridor it would be considered a communal kitchen, and assessed under 'Non-residential buildings - occupied spaces'.
Daylighting – requirements differing by area - KBCN0176
Where areas within a building have different daylighting requirements for the same credit, all relevant areas must meet the requirements to award the daylighting credit(s).
The aim is to improve daylight conditions in all applicable area types of an assessed building.
Daylighting – retail cafe / dining areas - KBCN0968
Customer seating/dining areas in a cafe or restaurant should be considered as 'sales areas'. Sales counters, staff areas or food preparation areas, for example, should be assessed as 'Other occupied areas' in accordance with the definition of 'Occupied space'..
The requirements for 'Sales areas' are applied to transient spaces.
Daylighting – side-lit internal association and atrium areas - KBCN1198
In buildings where the design of internal associations or atriums areas means that the space cannot be top-lit and is instead side-lit, the Daylighting criteria can be applied as follows;
Minimum values of average daylight factor:
The internal association or atrium area space will need to achieve an average daylight factor of 3% across a minimum of 80% of the space and either a uniformity ratio of 0.3 or a minimum point daylight factor of 0.9%.
The internal association or atrium area space will need to achieve a minimum daylight illuminance of at least 90 lux for 2650 hours per year.
Daylighting – studio flats - KBCN0808
In the case of studio flats, the minimum area of compliance for the average daylight factor requirement is based on the combined area of kitchen, living room, bed and study area. Circulation areas do not need to be included in the calculation.
Daylighting – uniformity ratio applicability - KBCN0584
The uniformity ratio requirements apply to the percentage of the building’s relevant areas specified in the table. In the NC 2013 scheme, this is 80%.
Daylighting – Floor areas for average daylight calculations - KBCN1081
Where the room size is comparable and the function is the same, such as ‘kitchen’, the percentage rule needs to be applied to the total floor area.
As the average daylight factor is a measure of daylight across the whole room, only whole rooms can be compliant. This is why we refer to rounding up the ‘80% of the floor area’ requirement to the rounded up number of compliant rooms.
This rule applies to rooms of a similar size and function and the Daylight issue calculations methodology includes a simple example, where all the rooms are the same size. However, this rule can still be applied to rooms of different sizes.
Spaces whose size is substantially larger should meet the average daylight factor requirement on their own. In these cases, the percentage requirement is still applicable to the floor area of the remaining rooms.
Where a building contains different area types (as identified in tables 5.1, 5.3, 5.8 and 5.9), the 80% minimum floor area must be calculated by each separate area type. For example, a multi-residential building that contained kitchen areas and living room areas would need both of these areas to comply with the 80% minimum floor area requirement separately.
This KBCN aligns with KBCN0471 of UKNC 2014
Dedicated cycle lanes/paths - KBCN1384
The term 'dedicated' is not intended to preclude cycle routes which are shared with pedestrians or vehicles. The assessor may deem such arrangements compliant, provided that they meet the requirements of the approved external guidance referred to in the criteria.
EFSA daylight requirements for Schools - KBCN1272
For school buildings, it is acceptable to use the Education and Skills Funding Agency (EFSA) framework requirements as an alternative method of compliance with the 'Daylighting' criteria. In this case, evidence would be required to demonstrate that the requirements in the framework have been adhered to. At least 80% of all relevant room types (weighted by area) must meet the relevant criteria in the ESFA
Reworded to clarify that the 80% requirement still applies. 31/07/2019
Emissions from construction products ISO 16000-10 - KBCN1134
Results of testing to ISO 16000-10 can be considered compliant with the relevant testing requirements of the emissions from construction products credit where the product manufacturer can demonstrate the results generated by testing to ISO 16000-10 correlate to results that would be achieved using EN 16516 or ISO 16000-9.
This is because EN 16516 classifies ISO 16000-10 as an ‘indirect method’, which means “any simplified, screening, secondary, derived or alternative method. An indirect method can be applied if it provides a result that is comparable to or that correlates with the result of the reference method under the conditions applied. The validity of the correlation with the reference method is limited to the field of application for which it has been established.”
Erratum – Table 1 in V2.5 of GN22: BREEAM and HQM recognised schemes for emissions from construction products - KBCN1436
Table 1 in V2.5 of GN22 has two footnote symbols missing:
• Product Type column – Paints and varnishes should read Paints and varnishes*
• Product Type column – Wood panels should read Wood panels^
These will be corrected in the next reissue of the Note.
Erratum – UK NC2018 Issue overview icons - KBCN1070
Some icons in the recently published UKNC2018 technical manual indicate incorrect numbers of credits available by assessment type. The table below summarises the error and correction needed.
10/08/18 - Technical manual updated. Only relevant to v1.0 of the manual
EU CLP Regulation and BREEAM Category 1A and 1B carcinogens emission limit criteria - KBCN1280
The European Regulation (EC) No.1272/2008 on classification, labelling and packaging of substances and mixtures (‘the CLP Regulation’ or ‘CLP’) applies to all EU Member States.
CLP requires manufacturers, importers, downstream users and distributors to communicate the identified hazards of a substance or mixture to the other parties in the supply chain, including to consumers. The regulation requires products with hazardous properties to be labelled in accordance with CLP before being placed on the market. CLP requires products containing any ingredients that have been classified as Category 1A and 1B carcinogens to be labelled as carcinogenic.
Therefore, with respect to the BREEAM Category 1A and 1B carcinogens emission limit criteria, for products marketed in EU Member States, if a product’s safety information (e.g. safety data sheet) or a manufacturer’s declaration confirms that that the product does not need to be labelled as a Category 1A or 1B carcinogen in accordance with CLP, then this information would be an acceptable form of evidence for demonstrating compliance with the criteria
Exemplary level credit - KBCN1131
The exemplary level credit of Hea 06 requires the use of a compliant risk based security rating scheme and for the projects performance against the scheme to be confirmed through independent assessment and verification.
Where this criteria has been met, and as such the exemplary level credit achieved, the 'Security of site and building' credit of Hea 06 is also automatically achieved. This is because the compliant risk based security rating scheme will cover the requirements of the 'Security of site and building' credit, in addition to covering many other aspects.
Exemplary level credit and Secured by Design (SbD) - KBCN1228
Secured by Design (SbD) cannot currently be considered compliant with the requirements of the exemplary level credit for this Issue which requires: ‘A compliant risk based security rating scheme has been used. The performance against the scheme has been confirmed by independent assessment and verification.’
This is for the following reasons:
- SbD police officers are not fully independent when providing design guidance to the end user, as they recommend the use of SbD ‘approved’ products.
- Recommendations from using SbD are proposed solutions taken from a prescriptive list of security measures/products. As such, there is no grading or rating provided at the end of the process.
- SbD is not a certification body and therefore does not provide independent assessment and verification.
External lighting – architectural façade lighting - KBCN0650
Architectural façade (or other decorative) lighting, which does not provide users with lighting to perform tasks outdoors, does not need to be included in the assessment of external lighting.
This Issue seeks to ensure that lighting levels are appropriate for tasks which building users will be undertaking outdoors.
Formaldehyde / VOC levels exceed prescribed limits - KBCN0258
If the measured formaldehyde / VOC concentrations were above the prescribed limits, the appropriate remedial action must be taken, as described in the IAQ Plan. The criterion requires confirmation of 'the measures that have or will be undertaken' however it does not specifically address re-testing. We would expect, however that the IAQ Plan should outline what remedial measures are appropriate depending upon the severity and type of the non-compliance with prescribed limits. Such measures may include re-testing as a matter of 'best practice'.
Where levels are found to exceed these limits, the project team confirms the measures that have, or will be undertaken in accordance with the IAQ plan, to reduce the TVOC and formaldehyde levels to within the above limits.
GN06 Hea 02 Indoor Air Quality Plan – BREEAM UK New Construction 2011 and 2014 - KBCN0618
It has been shown that poor indoor air quality is linked to health deterioration and poor performance of building occupants 1 and 2. For this reason BREEAM rewards projects that produce an Indoor Air Quality plan (IAQP) which seeks to minimise sources of pollution and optimise indoor air quality.
The purpose of this Guidance Note is to provide guidance to assessors and project teams regarding the content and rigour of an Indoor Air Quality Plan (IAQP) as required by the Hea 02 Indoor air quality criteria in the BREEAM New Construction and Refurbishment schemes. It should not be interpreted as BREEAM criteria. It is intended to provide assessors and project teams with further, flexible information and guidance regarding the rigour, content and tasks of an IAQP.”
View full Guidance Note
(licensed assessors only)
View all Guidance Notes
(licensed assessors only)
Updated text to reflect the latest version of this Guidance Note
GN22 Recognised schemes for emissions from building product - KBCN0719
Within the Health and Wellbeing category of a number of BREEAM schemes, credits are awarded for specifying materials that minimise emissions from building products, e.g. formaldehyde, volatile organic compounds (VOCs). These criteria involve meeting emission level performance requirements in accordance with compliant performance and testing standards. Similar criteria have been included in the Home Quality Mark (HQM) scheme. The purpose of this Guidance Note is to publish a list of schemes that show equivalent or better performance than the current BREEAM and HQM criteria, and therefore can be used to demonstrate compliance with the criteria. This note should be read in conjunction with the relevant assessment issue guidance provided in the appropriate BREEAM scheme or HQM technical manual.
View full Guidance Note
(licensed assessors only)
View all Guidance Notes
(licensed assessors only)
12/03/2018 Link to Guidance Note updated
25/01/2019 Link to Guidance Note updated
Historic buildings – paints and varnishes - KBCN1041
An exemption is allowed for extensions to historic buildings where there is an explicit requirement from the Local Authority conservation officer or the national conservation body (i.e. English Heritage, Historic Scotland, CADW in Wales and NIEA:HBU in Northern Ireland) to use specific paints and varnishes, which may contain a high level of VOCs or fall within the scope of the Volatile Organic Compounds in Paints, Vanishes and Vehicle Refinishing Products Regulations 2012. This is allowable for grade I and II* listed buildings in England and Wales and grade A and B+ listed buildings in Scotland and Northern Ireland. In all cases, procedures should be in place to ensure the building is flushed out for a sufficient period prior to occupation and adequately ventilated, in order to reduce the risks associated with VOCs, in accordance with the criteria.
Indoor air quality – single room MVHRs - KBCN1042
Single room mechanical ventilation heat recovery units are exempt from the requirement to demonstrate that the air intake and exhaust are a suitable distance apart. However, it must still be demonstrated that the air intakes of such units are suitably located to minimise the ingress of other potential external pollutants.
Indoor air quality plan - KBCN0294
The Indoor Air Quality Plan does not have prescriptive criteria as it is recognised that each building will have differing conditions/user requirements. There is flexibility for the design team to use their professional judgement to determine what is appropriate to meet the criterion, subject to the plan addressing the relevant items as listed within the Technical Manual.
Indoor air quality plan – RIBA stage requirement - KBCN1206
In Issues 1.0 and 1.2 of the technical manual, the prerequisite requires the Indoor air quality plan to be produced no later than the end of Concept Design.
Clarification of the requirements in Hea 02:
The prerequisite currently states:
‘1. A site-specific indoor air quality plan has been produced and implemented in accordance with the guidance in Guidance Note GN06. The plan must be produced no later than the end of Concept Design. The objective of the plan is to facilitate a process that leads to design, specification and installation decisions and actions that minimise indoor air pollution during occupation of the building…’
‘1 A site-specific indoor air quality plan has been produced and implemented in accordance with the guidance in Guidance Note GN06. The objective of the plan is to facilitate a process that leads to design, specification and installation decisions and actions, which minimise indoor air pollution during occupation of the building…:’
This will be confirmed in the next re-issue of the technical manual, but can be applied immediately in all issues of the UK NC2018 scheme.
Industrial buildings – operational areas - KBCN1342
The aim of this issue is to encourage a healthy internal environment. For the operational areas of industrial buildings, the internal environment is dictated by health and safety requirements. This means that the BREEAM requirements should not be made applicable to them, and so the operational areas can be ignored in the assessment of Hea 02.
No relevant areas for room acoustics - KBCN1291
Where a building does not have areas relevant to the 'room acoustics' criteria, the credit available for room acoustics can be awarded by default where the building complies with the indoor ambient noise levels and the sound insulation criteria.
Off-site manufactured installations – internal finishes - KBCN0137
Internal finishes in off-site manufactured installations such as lifts need to be assessed for the VOC criteria.
The specification of internal finishes (regardless of whether they are installed on site or in the factory) will impact on VOC emissions. By specifying low VOC finishes, design teams will be encouraging manufacturers to consider the environmental impacts of their products.
Office areas in education buildings – Relevant ventilation standard - KBCN0223
All education buildings should comply with BB101 Ventilation of school buildings, which confirms a ventilation rate for offices.
Outdoor space – shared with other buildings - KBCN1045
Where a building has existing external space, or will be developing new external space, that is or will be shared with other buildings, this can be deemed acceptable if the space meets the definition of ‘Outside space’ and is of a size able to cater for the building users of all the associated buildings.
Paints for specialist applications - KBCN0872
Where a paint or coating does not fall within one of the categories in Annex II of the EU Directive 2004/42/CE or the categories in the relevant tables of the technical manuals (for schemes where the Directive is not applicable), then the paint or coating does not need to be assessed.
16/06/2017 KBCN extracted from existing KBCN0212.
13/03/2020 KBCN amended to clarify exceptions and applicability
PMV and PPD reporting for mixed mode ventilation buildings - KBCN0632
When assessing buildings where both naturally ventilated and air conditioned spaces are included, reporting the PMV and PPD indices is required.
Pre-requisite – Indoor air quality (IAQ) plan after Concept Design stage - KBCN1155
Where the Indoor Air Quality Plan has been produced after the Concept Design stage credits may still be achievable for this issue. Provided that it can be demonstrated that the IAQP has influenced the design and that the late production of the IAQP has not hindered the ability to influence the design and specification of products this would be acceptable to meet this requirement.
Remedial works – timing of acoustic re-testing - KBCN1164
The intent of CN "Remedial works" is that, where these are required, re-testing is carried out prior to handover and occupation.
However, it is permissible to carry out the re-testing post-occupation. This is provided any specific guidance for particular building types related test conditions have been met (for instance, it may be that some building specific guidance requires furniture or carpets to not be present during the testing).
Compliance cannot be achieved based on a letter from the SQA confirming that the contractor has followed their advice to achieve the required performance.
07.11.18 KBCN amended to allow for re-testing to be carried-out post-handover.
Reporting PPD and PMV Figures - KBCN0867
The individual carrying out the modelling should be able to provide values for both the PMV and PPD for the building.
The PMV and PPD values need to be reported, in the scoring & reporting tool, for data recording purposes.
The values to report are the observed range of values for PMV and PPD across all occupied areas across all the hours when these are expected to be occupied (enter the minimum and maximum for each i.e. PMV = 0.2 - 0.5, PPD = 10 - 15%).
However, if compliance with the thermal comfort criteria is demonstrated without using a full dynamic thermal analysis software package and via a less complex system, which does not generate the required PMV/PPD metrics, these do not have to be provided.
Robust Details – Testing requirements - KBCN1251
For self-contained dwellings, which form part of a Multi-residential assessment, compliance can be demonstrated where the use of constructions for all relevant building elements have been registered with and assessed and approved by Robust Details Limited (RDL) and found to achieve the performance standards required for the number of credits sought.
Robust Details (RDs) are construction solutions that provide an alternative to pre-completion sound insulation testing as a method of complying with Requirements E1 of Approved Document E (2003 Edition) of the Building Regulations (England and Wales), DOE Technical Booklet G - Sound 2012 (Northern Ireland) and Technical Handbook Section 5 - Noise, 2013 (Scotland). The relevant plots on a development must be registered with RDL and built in accordance with the RD specification. To give a reasonable level of assurance that these details will achieve the required minimum standards, RDL carry out random inspections during construction and random sound insulation tests after construction. A Robust Detail is deemed to be approved for BREEAM (Multi-residential building) credits only when it achieves a specified performance level as assessed by RDL. Robust Details can only be used in relation to assessment for new build dwellings and cannot be used to assess the performance of construction details in rooms for residential purposes or material change of use.
Safe access – vehicle delivery routes - KBCN1046
Vehicle delivery routes which cross cycle or pedestrian routes may be acceptable provided there are adequate physical control measures in place to ensure safe access and thus minimise the possibility of delivery vehicles coming into conflict with cyclists and pedestrians.
Examples of such measures could be vehicle barriers or retractable vehicle bollards, which only allow access to delivery vehicles when required and whose operation and controls account for cycle and pedestrian movements.
18 Mar 2021 wording clarified
07.06.2018 Intent and wording clarified.
Security – Change of SQSS and recommendations - KBCN1044
If the SQSS working on the project changes during the assessment, the recommendations of the original SQSS can be modified if the new SQSS can provide justification for this.
Testing laboratory certification - KBCN1337
Where an organisation used for sampling and analysis of indoor air or for analysis of emissions from building products is not accredited to ISO / IEC 17025, the organisation must be accredited either by a national accreditation body, or by a member of any one of the following accreditation groups:
European Cooperation for Accreditation
International Accreditation Forum
International Laboratory Accreditation Cooperation
The accreditation must specifically covering sampling and analysis of indoor air or analysis of emissions from building products.
For indoor air sampling, alternative qualifications/accreditation to ISO 17025 (or the listed accreditations) could be considered compliant where this demonstrates that the organisation/individual performing the sampling has a suitable level of competence and experience. Any alternative qualifications will need to be reviewed through a technical query.
07/05/2021: Added clarification regarding alternative qualifications
10/05/2021: Updated scheme applicability
Thermal comfort – Changing rooms - KBCN1133
Whilst thermal comfort in changing rooms may be considered as significant, such spaces are, generally, outside the scope of this Issue, as they would not fall within the definition of an 'occupied space'.
17/06/2019 - This supersedes the advice previously provided in this KBCN, which was published in error on 13/06/2018
Thermal modelling – naturally ventilated buildings with heating for the winter months - KBCN1345
Where naturally ventilated occupied spaces are heated in the winter/heating season, as an alternative to demonstrating compliance with the winter operative temperature ranges in CIBSE Guide A or other appropriate industry standard, such occupied spaces can demonstrate compliance through meeting the Category B requirements for PPD, PMV and local discomfort set out in Table A.1 of Annex A of ISO 7730:2005. Where this alternative compliance route is used, when these naturally ventilated occupied spaces are in ‘free-running mode’ (i.e. outside of the winter/heating season), it is not possible to use the ISO 7730:2005 method and therefore these spaces must demonstrate compliance with the requirements to limit the risk overheating in accordance with CIBSE TM52.
Thermal modelling for large scale projects - KBCN1171
In cases where the scale of the project makes it unfeasible to provide thermal modelling for every space, it is acceptable to demonstrate compliance with a representative sample of floors or rooms, ensuring any worst case scenarios are included.
Thermal modelling – buildings with mixed-mode ventilation - KBCN1346
Where a building has some occupied spaces that are naturally ventilated and some occupied spaces that are air-conditioned, the thermal modelling must demonstrate that the naturally ventilated spaces meet the criteria for naturally ventilated buildings and that the air-conditioned spaces meet the criteria for air-conditioned buildings.
Ventilation – Window opening restrictors - KBCN1032
Window openings in certain buildings or building areas may need to have restricted opening distances (for Healthcare buildings, in accordance with HBN 00-10 Part D: Windows and associated hardware (235) or as required by Building Control). This is generally for health and safety reasons, especially in high-rise buildings or where windows are within reach of the elderly, mentally ill or children. For BREEAM however, it is considered that such limitations can be overcome in order to provide compliant natural ventilation solutions.
View out – applicable areas - KBCN0268
The aim of the View out credit is to allow occupants to refocus their eyes from close work.
The view out criteria are not applicable to occupied areas such as meeting rooms, where typically close work is not undertaken and there are no permanent workstations.
Where rooms contain areas of different functions, only those areas that are applicable should be included in the assessment. In this case a notional line can be drawn on the plans and calculations made based on these applicable areas only.
View out – eye level - KBCN0581
BREEAM defines an adequate view out as being at seated eye level (1.2 – 1.3m) within the relevant building areas. However, where occupants will not have the option to be seated, for example in some industrial operational areas where the work being undertaken requires occupants to remain standing, the height of the view out can be changed accordingly to suit the eye level of occupants. All other view out requirements have to be met and clear justification provided for changing the height/level of the view out.
In some relevant building areas, occupants may not be sitting down to undertake tasks. Allowing the view out height requirements to be changed accordingly ensures building occupants gain maximum benefit from the view out.
View Out – First Aid Rooms - KBCN1104
The view out criteria do not apply to dedicated first aid or medical rooms in non-healthcare projects.
BREEAM recognises the need for user privacy in such areas and that these are intermittently occupied.
View out – internal view within an atrium - KBCN1240
Where the criteria are otherwise met, an internal view across an unobstructed atrium void can be considered compliant.
Internal views are generally not acceptable, however where it is physically impossible to obstruct the view with partitions, equipment or furniture, this can be accepted at the discretion of the assessor.
View out – no relevant areas - KBCN0876
If the scope of the assessment does not include any relevant building areas, as defined within the manual, the criteria for 'view out' can be considered as met by default.
Only spaces that fall within the definition of relevant areas and are within the assessment's scope need to be assessed.
View out – percentage area - KBCN0166
For the view out credit, compliance must be demonstrated for the percentage of the floor area in each relevant building area, rather than the percentage of the total relevant building area in the building.
14/2/17 Wording amended to clarify that the percentage must be achieved for each 'relevant building area'.
View out – rooms used for security or other critical functions - KBCN1040
The View out criteria are not applicable to rooms containing security or critical systems or sensitive material, such as CCTV monitoring rooms.
Where it can be demonstrated that the presence of compliant windows would compromise a critical function of the space, the criteria can be considered not applicable.
View out – Shell only/Shell & Core - KBCN1354
Where it is not possible to confirm which areas of the building will contain workstations/benches or desks, then all areas of the building designed for and/or likely to be occupied by workstations/benches or desks must comply with the relevant criteria.
View out for commercial kitchens - KBCN1216
It is not necessary to provide a view out for commercial kitchens. This is because in such a space it is likely that kitchen staff will move around, doing various tasks. This makes the requirements for the view out to rest the eyes unnecessary.
Zoning and control – dimming - KBCN1018
Localised dimming controls installed in line with the criteria, along with a master on/off switch, can be considered as meeting the aim of the requirement for 'controls' in open plan offices.
The aim is for occupants to have local control over their lighting and maintain comfortable lighting levels.
Zoning and control – PIR in circulation spaces - KBCN0332
PIR controls can be deemed compliant in circulation spaces such as corridors. In this instance 'separate occupant controls' are not required.
The requirement for user control is so that the building users can have direct control over their immediate work environment to ensure it is suitable for their personal needs. In circulation spaces, occupancy is transient and PIR control in these spaces is acceptable.
Zoning and occupant control – access to lighting controls - KBCN00032
In building areas where building users, for example the general public, are not expected to have access to lighting controls, these areas can be excluded from the assessment.
The aim of these criteria is to increase user control of lighting. Where user control is not applicable, such as on a shop floor, the criteria should not be applied.
Zoning and occupant control – control via BMS - KBCN0703
Occupant control via a BMS is not normally considered a compliant BREEAM solution. Any solution that requires the action of a third party (eg facilities manager) is not considered under the control of the occupant. Solutions where all relevant building occupants have control via a user-interface via BMS may be considered compliant where the assessor is satisfied that the aim of the criteria are met.
User-control must be available directly to the occupant.
01/08/2017 - KBCN applicability to Thermal comfort Issue removed.
Zoning and occupant control – PIR detection systems - KBCN0335
The aim of the Health & Wellbeing category is to recognise ways to benefit occupants through giving them control of their lighting environment. Without manual overrides, presence or absence detection lighting controls (such as PIR detection systems) are not compliant with the criteria.
BREEAM recognises the energy efficiency benefits of detection systems in buildings through the Energy category. In some cases, the design team may have to prioritise one particular lighting strategy to the detriment of achieving a credit elsewhere.
28 04 2021 Wording amended to include absence detection systems.
18 09 2017 Wording amended to clarify the meaning.
Zoning and occupant control – whiteboards and display screens - KBCN1433
Whiteboards and display screens in dedicated teaching or presentation spaces require separate zoning and control for lighting, as specified in the criteria.
Lighting around whiteboards and display screens which are typically found in general office areas, meeting rooms, or in other generic spaces do not require separate zoning and control to meet the criteria. In such cases, the assessor should provide justification.
Whiteboards and display screens in dedicated teaching / presentation spaces are likely to be used frequently, and require appropriate zoning and control. An increasing number of offices and meeting rooms now include display screens - however separate zoning and control may not be appropriate.
Zoning and occupant controls – handheld remote controls - KBCN1243
Remote control light switches can be considered as compliant, on the basis that these are provided in sufficient numbers/locations to meet the aim of the criteria.
[KBCN withdrawn] ~ Daylighting – Education buildings - KBCN1031
This KBCN has been withdrawn and replaced with the more detailed KBCN1272.
KBCN withdrawn on 13/08/2019:
Where the requirements of Education and Skills Funding Agency Generic Design Brief, November 2017. Technical Annex 2E ‘Daylight and electric lighting’, have been demonstrably met, the BREEAM daylighting requirements can be deemed to have also been met. The two credits for daylighting can be awarded.
Information correct as of 23rdJune 2021. Please see kb.breeam.com for the latest compliance information.
[KBCN withdrawn] ~ Ventilation – BB101 - KBCN1242
This KBCN has been withdrawn and is no longer valid.
This is because Building Bulletin 101 was updated in August 2018.
KBCN withdrawn on 04/02/2019:
The web page that hosts the currently active version of Building Bulletin 101: ventilation for school buildings, available here, states that the document was published on 11th March 2014. However, when opening the document itself, the publishing date refers to '5th July 2006'.
The current version of the standard which should be used is Version 1.4 dated 5th July 2006 within the document.